Removing Headspace Restriction Saves Thousands for Hillsborough County, Florida
Abstract:Hillsborough County Public Utilities Department, with the assistance of Siemens, identified and eliminated a hydraulic restriction in a gravity sewer upstream of a master pump station.
Identifying the restriction required careful observation of site conditions and 24-hour analysis of atmospheric pressure in the sewer. Once identified, the restriction was eliminated by adjustment of wet well levels at the Master Pump Station. This adjustment allowed odorous air in the gravity sewer to be conveyed to the vapor-phase odor control system at the pump station and resulted in complete elimination of upstream chemical addition for odor control.
Document Type: Research Article
Publication date: January 1, 2012
More about this publication?
- Proceedings of the Water Environment Federation is an archive of papers published in the proceedings of the annual Water Environment Federation® Technical Exhibition and Conference (WEFTEC® ) and specialty conferences held since the year 2000. These proceedings are not peer reviewed. WEF Members: Sign in (right panel) with your IngentaConnect user name and password to receive complimentary access.
- Subscribe to this Title
- Membership Information
- About WEF Proceedings
- WEFTEC Conference Information
- ingentaconnect is not responsible for the content or availability of external websites