Facility Assessment Provides Significant O&M Savings at the Water Replenishment District;amp;#x0027;s Vander Lans Water Treatment Facility
Abstract:The Water Replenishment District commissioned the Leo J. Vander Lans (LJVL) facility in 2003 to supplement their imported water supply used to protect drinking water aquifers in the Central Basin of Los Angeles County. Unfortunately, this facility has been experiencing significant RO fouling since the facility start-up and a facility assessment was needed to determine the cause and recommend process changes to improve operations. This paper presents the results of this assessment which consisted of documenting: (1) microfiltration system performance and filtrate water quality (2) analyze the RO feed water quality to determine the most likely RO foulant(s), (3) assessment of RO performance, and (4) document the resulting recommended process changes. This paper will conclude with a comparison of the membrane fouling rate prior to and after implementing the recommended process changes.
Document Type: Research Article
Publication date: 2009-01-01
More about this publication?
- Proceedings of the Water Environment Federation is an archive of papers published in the proceedings of the annual Water Environment Federation® Technical Exhibition and Conference (WEFTEC® ) and specialty conferences held since the year 2000. These proceedings are not peer reviewed. WEF Members: Sign in (right panel) with your IngentaConnect user name and password to receive complimentary access.
- Subscribe to this Title
- Membership Information
- About WEF Proceedings
- WEFTEC Conference Information
- Ingenta Connect is not responsible for the content or availability of external websites