Fixed Media IFAS in Contact Stabilization Zone
Abstract:The City of Coeur d'Alene wastewater treatment plant is operating at its capacity, yet continue to increase and lower ammonia limits are looming for 2009 or 2010. The planned facility expansion won't be online until 2014.
During spring of 2008, five 30,000 ft2of IFAS media were installed to test the potential of integrated fixed film activated sludge (IFAS) to improve nitrification. Because this facility is a trickling filter/contact stabilization (TF/CS) plant, the success of an IFAS upgrade was not certain due to the short hydraulic retention time and a low achievable suspended growth SRT.
The results from the first season were encouraging. Once the process stabilized, the monthly average effluent ammonia concentration was lower than during any month in recent years. Taking into account the change in plant loading and the additional ammonia reduction, the estimated nitrification capacity of the installed IFAS media was between 80 lb/d and 120 lb/d in September 2008. Additional media was installed in May 2009.
Document Type: Research Article
Publication date: January 1, 2009
More about this publication?
- Proceedings of the Water Environment Federation is an archive of papers published in the proceedings of the annual Water Environment Federation® Technical Exhibition and Conference (WEFTEC® ) and specialty conferences held since the year 2000. These proceedings are not peer reviewed. WEF Members: Sign in (right panel) with your IngentaConnect user name and password to receive complimentary access.
- Subscribe to this Title
- Membership Information
- About WEF Proceedings
- WEFTEC Conference Information
- Ingenta Connect is not responsible for the content or availability of external websites