Replacement of medium voltage variable frequency drive (VFD) systems originally installed in the early 1990s was evaluated to determine if recent advancement in technology would benefit the owner/operator at two large raw wastewater pump stations at Boston's Deer Island wastewater
treatment plant. Each of the two cases evaluated involved VFD systems controlling vertical synchronous brushless motors driving raw wastewater lift pumps. Case #1 involved eight 1250-hp synchronous motors with dual 1100 VAC windings, 2200 VAC, 400 rpm, 60 Hz. Case #2 involved ten 3500-hp
synchronous motors with dual 2200 VAC windings, 2200 VAC, 400 rpm, 60 Hz. The Case #1 VFD system was successfully replaced with state-of-the-art voltage source pulse-width modulating (PWM) drive technology coupled with reconfiguring the two 1100 VAC windings of the existing motors to operate
the motor and new VFD system at 2200 VAC. This VFD system replacement is providing increased reliability, efficiency, enhanced power factor, reduced power consumption, and reduced maintenance cost. The Case #2 VFD system replacement is currently in the design phase based on new synchronous
motors and PWM drives.
Proceedings of the Water Environment Federation is an archive of papers published in the proceedings of the annual Water Environment Federation® Technical Exhibition and Conference (WEFTEC® ) and specialty conferences held since the year 2000. These proceedings are not peer reviewed. WEF Members: Sign in (right panel) with your IngentaConnect user name and password to receive complimentary access.