Biofiltration of High-Strength Exhaust from Biosolids Composting: Lessons Learned and Demonstration of Successful Treatment
Abstract:The Solid Waste Authority of Palm Beach County, Florida, operates an in-vessel composting facility that processes 30 dry tons/day of dewatered biosolids combined with shredded yard waste. The facility consists of 36 aerated agitated bays in three buildings supplied by International Processes Systems (Now Siemens Water Technology). All exhaust air from the buildings is treated in three 60,000 cfm biofilter cells. New biofilter cells were commissioned in December 2002. Design and construction included some innovative features including: use of locally available limestone for the support plenum, use of locally available finely ground bark mulch in the media, a pre-humidification system with air-atomizing nozzles, clean-outs for every perforated lateral, and a fast-track design-build method of delivery.
After start-up the well water used for humidification caused rapid scaling of the laterals, due to the high mineral content and high evaporation efficiency. Pre-humidification was discontinued while a water softening and deionization system was under consideration. Since then the filters have been operated only with surface irrigation. The most recent rounds of performance testing have indicated that surface irrigation, combined with rainfall, were sufficient to maintain optimal moisture content throughout the full depth of media. Without pre-humidification, the irrigation distribution pattern is critical.
The filters have been periodically tested for odor and ammonia removal, most recently in 2006 and scheduled again for 2007. The filter media in the different cells have been in continuous use for 2.6 to 3.1 years. Typical inlet conditions were:
Temperature: dry-bulb range 96-105 deg. F. wet-bulb range 86-92 deg F.
Ammonia: 22 – 40 ppm
Hydrogen sulfide and methyl mercaptan: neglible or non-detect
Odor concentration: 1,500 – 2,400 D/T, using the prEN 13725 olfactometry standard.
The biofilters have consistently removed 100 % of ammonia and 93 – 98 % of odor with outlet odor concentrations in the range of 66 to 86 D/T. Thus, the biofilter is showing highly effective performance, despite the high temperature and moisture deficit in the inlet air. As a result, the composting facility is no longer a significant source of off-site odors.
Ammonia is an alkaline gas and there little acid gas present. The media has a pH in the range of 4.8 – 6.8. The acidic pH indicates that alkalinity is being consumed as a result of nitrification. A nitrogen mass balance indicated that the biofilters are operating in steady state rather than accumulating nitrogen, and that nitrogen leaves the biofilters by way of leachate and denitrification. Denitrification was demonstrated by the detection of nitrous oxide. Nitrous oxide is of increasing interest due to its effect as a greenhouse gases.
Document Type: Research Article
Publication date: 2008-01-01
More about this publication?
- Proceedings of the Water Environment Federation is an archive of papers published in the proceedings of the annual Water Environment Federation® Technical Exhibition and Conference (WEFTEC® ) and specialty conferences held since the year 2000. These proceedings are not peer reviewed. A subscription to the Proceedings of the Water Environment Federation includes access to most papers presented at the annual WEF Technical Exhibition and Conference (WEFTEC) and other conferences held since 2000. Subscription access begins 12 months after the event and is valid for 12 months from month of purchase. A subscription to the Proceedings of the Water Environment Federation is included in Water Environment Federation (WEF) membership.
WEF Members: Sign in (right panel) with your IngentaConnect user name and password to receive complimentary access. Access begins 12 months after the conference or event
- Subscribe to this Title
- Membership Information
- About WEF Proceedings
- WEFTEC Conference Information
- Learn about the many other WEF member benefits and join today
- Ingenta Connect is not responsible for the content or availability of external websites