INTEGRATED RECIP® WATER TREATMENT SYSTEM WITH U.V. DISINFECTION FOR DECENTRALIZED WASTEWATER TREATMENT: PART I: MICROBIAL DYNAMICS
A novel wastewater treatment system (ReCip®), developed for on-site and decentralized treatment of domestic wastewater, was modified by installing either low pressure-low intensity 25 and/or 65 watt U.V. lights into the systems pumping operation. This modification enabled the wastewater to be exposed to low intensity U.V. light up to 24 times per day. In addition, two subsurface-flow constructed wetlands were installed down-gradient from the ReCip-U.V. treatment unit to facilitate removal of nitrate and to evaluate re-growth of indicator organisms (E.coli and Enterococcus). The integrated system treated from 200 to 400 gallons (0.87 m3 influent ± 0.266 m3/day) of wastewater each day. It was hypothesized that this new ReCip® U.V. configuration could be effective and less costly than conventional one-pass U.V. disinfection systems because of the long hydraulic retention time (2-3 days), and the recurrent exposure of pathogens to low intensity U.V. lights. Over the course of these studies, three different light-position configurations and two wattages were tested. During the final six months of monitoring, the reciprocating U.V. light configuration (65 watt lamps in each of cells C and D), resulted in 3-5 log reductions of E.coli and Enterococcus. In most instances, E.coli levels were reduced to less than 5 cells/100 mL of treated effluent. The use of U.V. did not impact wastewater treatment and the integrated ReCip-U.V. system provided excellent wastewater treatment with respect to removal of suspended solids, odor, turbidity, chemical oxygen demand (COD), TKN and ammonia-nitrogen. Treated wastewater was clear, odor free, with low concentrations of indicator bacteria, organic matter, and nitrogen. Based on results of the twenty two month study, it is recommended that the system have two 65 watt U.V. lights, one in each of the last two ReCip® treatment cells (C and D), and that the ReCip® system be operated such that the wastewater is exposed to U.V. lights from 12 to 24 times per day.
No Reference information available - sign in for access.
No Citation information available - sign in for access.
No Supplementary Data.
No Article Media
Document Type: Research Article
Publication date: 01 January 2007
More about this publication?
- Proceedings of the Water Environment Federation is an archive of papers published in the proceedings of the annual Water Environment Federation® Technical Exhibition and Conference (WEFTEC® ) and specialty conferences held since the year 2000. These proceedings are not peer reviewed. A subscription to the Proceedings of the Water Environment Federation includes access to most papers presented at the annual WEF Technical Exhibition and Conference (WEFTEC) and other conferences held since 2000. Subscription access begins 12 months after the event and is valid for 12 months from month of purchase. A subscription to the Proceedings of the Water Environment Federation is included in Water Environment Federation (WEF) membership.
WEF Members: Sign in (right panel) with your IngentaConnect user name and password to receive complimentary access. Access begins 12 months after the conference or event
- Subscribe to this Title
- Membership Information
- About WEF Proceedings
- WEFTEC Conference Information
- Learn about the many other WEF member benefits and join today
- Ingenta Connect is not responsible for the content or availability of external websites