EVALUATION OF THE SAFETY AND EFFICACY OF CHLORINE DIOXIDE FOR LEGIONELLA CONTROL IN HOSPITAL WATER SYSTEMS
Chlorine dioxide (ClO2) has been used recently in the U.S. for disinfection of hospital water systems to prevent hospital-acquired Legionnaires' disease. The Environmental Protection Agency Maximum Residual Disinfectant Level for chlorine dioxide is 0.8 mg/L. The EPA Maximum Contaminant Level (EPA MCL) for chlorine dioxide disinfection byproduct-chlorite is 1.0 mg/L. The level of chlorite (ClO2 −) generated during continuous chlorine dioxide disinfection of hospital water system has not been well studied. In a 31-month prospective study, we evaluated the efficacy of chlorine dioxide to control LEGIONELLA in a hospital water system and monitored the levels of ClO2 and ClO2 −. LEGIONELLA positivity was 60% (12/20) in hot water in August 2003, and was reduced to 10% (2/20) in February 2006. An extended time (18 months) was needed to achieve a significant reduction of LEGIONELLA positivity in hot water due to low chlorine dioxide residual in the hot water system. When ClO2 was injected into the cold water main at 0.5-0.7 mg/L, the mean concentration (mg/L) of ClO2 and ClO2 − in cold water samples were 0.42 and 0.28, respectively, while the concentrations in hot water samples were 0.07 and 0.42, respectively. The chlorine dioxide concentration in the hot water was significantly lower than in the cold water (p<0.05). Mean ClO2 residual and chlorite concentrations did not exceed the EPA MRDL of 0.8 mg/L and MCL of 1.0 mg/L, respectively. The use of the chlorine dioxide for controlling LEGIONELLA in this hospital water system was safe based on the MRDL of chlorine dioxide and MCL of chlorite.
No Reference information available - sign in for access.
No Citation information available - sign in for access.
No Supplementary Data.
No Article Media
Document Type: Research Article
Publication date: 01 January 2007
More about this publication?
- Proceedings of the Water Environment Federation is an archive of papers published in the proceedings of the annual Water Environment Federation® Technical Exhibition and Conference (WEFTEC® ) and specialty conferences held since the year 2000. These proceedings are not peer reviewed. A subscription to the Proceedings of the Water Environment Federation includes access to most papers presented at the annual WEF Technical Exhibition and Conference (WEFTEC) and other conferences held since 2000. Subscription access begins 12 months after the event and is valid for 12 months from month of purchase. A subscription to the Proceedings of the Water Environment Federation is included in Water Environment Federation (WEF) membership.
WEF Members: Sign in (right panel) with your IngentaConnect user name and password to receive complimentary access. Access begins 12 months after the conference or event
- Subscribe to this Title
- Membership Information
- About WEF Proceedings
- WEFTEC Conference Information
- Learn about the many other WEF member benefits and join today
- Ingenta Connect is not responsible for the content or availability of external websites