Chemically Enhanced Primary Treatment for a Large Water Reclamation Facility on a Constricted Site – Considerations for Design, Start-Up, And Operation
Abstract:To provide greater treatment capacity and to meet new water quality criteria for discharge to the Chattahoochee River, Cobb County Water System (CCWS) construction a new 60 million gallon per day (mgd) liquid treatment facility at the R.L. Sutton Water Reclamation Facility (Sutton WRF). A restricted site (25 acres) combined with an effluent limit on total phosphorus of 0.5 mg/L resulted in the decision to use chemically enhanced primary treatment (CEPT) to both minimize facility footprint and to provide phosphorus removal. Based on performance between May 2005 and April 2006, the new CEPT process facility at the Sutton WRF is removing over 50% of the influent 5-day biochemical oxygen demand (BOD5), over 60% of total suspended solids (TSS), and nearly 50% of the influent phosphorus. Jar settling tests performed during design indicated improved performance with chemical coagulation, and rapid mix and flocculation basins were provided prior to circular primary clarifiers. The primary coagulant is currently ferrous chloride, however, no polymer is used at this time. Although the facility is hydraulically under-loaded, it is meeting strict effluent limits with a low coagulant dose.
Document Type: Research Article
Publication date: 2006-01-01
More about this publication?
- Proceedings of the Water Environment Federation is an archive of papers published in the proceedings of the annual Water Environment Federation® Technical Exhibition and Conference (WEFTEC® ) and specialty conferences held since the year 2000. These proceedings are not peer reviewed. WEF Members: Sign in (right panel) with your IngentaConnect user name and password to receive complimentary access.
- Subscribe to this Title
- Membership Information
- About WEF Proceedings
- WEFTEC Conference Information
- Ingenta Connect is not responsible for the content or availability of external websites