If you are experiencing problems downloading PDF or HTML fulltext, our helpdesk recommend clearing your browser cache and trying again. If you need help in clearing your cache, please click here . Still need help? Email firstname.lastname@example.org
The influent pump station at Singapore's new Changi Wastewater Reclamation Plant is the first process operation to come on line. The odor control system is housed in one of the 37 m diameter influent pump shafts, 14 meters below ground level. Odor control is provided by two 10,000 cfm
multistage chemical scrubber systems followed by vertical bed, V-bank carbon adsorbers. Additional ventilation and odor control is provided intermittently as needed by a 65,000 cfm multi-stage odor control scrubber and V-bank carbon adsorber. Installation, commissioning and performance testing
have been completed, demonstrating better than 99.99% H2S removal at concentrations up to 500 ppm. An advanced on-line H2S monitoring system provides continuous measurement of the H2S concentration at the inlet, and at the outlet of each chemical scrubber
and each carbon adsorbrer. The H2S analyzer has resolution down to 0.002 ppm, and utilizes dilution probes for sampling at higher concentrations.
Proceedings of the Water Environment Federation is an archive of papers published in the proceedings of the annual Water Environment Federation® Technical Exhibition and Conference (WEFTEC® ) and specialty conferences held since the year 2000. These proceedings are not peer reviewed. WEF Members: Sign in (right panel) with your IngentaConnect user name and password to receive complimentary access.