UPDATE ON PURE OXYGEN FOR ODOR CONTROL AT THE TRINITY RIVER AUTHORITY OF TEXAS
Abstract:The Trinity River Authority of Texas (TRA or Authority) owns and operates the 162 MGD Central Regional Wastewater Treatment Plant (CRWS) in Grand Prairie, Texas. The plant is an advanced secondary facility consistently producing nitrified effluent with BOD and TSS concentrations less than 5 mg/L each and an ammonia nitrogen concentration less than 0.5 mg/L. In addition to providing high quality effluent, the Authority is committed to being a good neighbor to the commercial, recreational, and residential areas surrounding the plant. As such, the Authority has committed significant funds and manpower to minimizing the emission of odors from the plant.
In projects spanning more than 20 years, the plant has eliminated or minimized emissions from major odor sources such as the preliminary treatment areas, influent junction boxes, primary clarifier weirs, and sludge processing areas. The plant eliminated use of its sludge-only landfill except for screenings and went to beneficial reuse of all its sludge. The next phase of odor control would include the management of odors from aerated grit units and the quiescent areas of the primary clarifiers. Covering the primary clarifiers could involve literally acres of covers and the collection and treatment of well over 150,000 cfm of foul air.
As an alternative to the covering of the primary clarifiers and collection and treatment of the air, the Authority, with Alan Plummer Associates, Inc., conducted “full-scale pilot studies” to investigate the feasibility of using pure oxygen for odor control. Pure oxygen has been used for odor control in pressure lines in collection systems and in receiving streams to boost oxygen concentrations during critical low-flow periods. Use of pure oxygen for odor control at a wastewater treatment plant, however, is a new application.
Following the success of the pilot study, equipment for injecting oxygen was selected. Equipment selection was dependent on achieving the high dissolved oxygen concentration necessary for a successful project and efficiency of the equipment for dissolving oxygen. Even a slight drop in efficiency will cause a large increase in operating expenses. To identify optimum dosage rates and injection points, a second bench scale study was conducted. This study identified the reaction rate of sulfide oxidation for the wastewater stream. Identifying the reaction rate resulted in a projected savings of 4.7 million for initial construction costs and 183,000 in yearly operational costs. This paper provides a brief background on the previous pilot testing, and details results of the bench scale testing. Design related issues and equipment selection are also discussed.
Document Type: Research Article
Publication date: January 1, 2006
More about this publication?
- Proceedings of the Water Environment Federation is an archive of papers published in the proceedings of the annual Water Environment Federation® Technical Exhibition and Conference (WEFTEC® ) and specialty conferences held since the year 2000. These proceedings are not peer reviewed. WEF Members: Sign in (right panel) with your IngentaConnect user name and password to receive complimentary access.
- Subscribe to this Title
- Membership Information
- About WEF Proceedings
- WEFTEC Conference Information
- Ingenta Connect is not responsible for the content or availability of external websites