Application of the Proposed UVDGM Requirements to an Existing UV Disinfection Installation
Abstract:The Clayton County (Georgia) Water Authority (CCWA) has installed UV disinfection systems at three water production plants (WPPs). The CCWA's projects were designed, constructed, and tested in advance of the publication of the Proposed Ultraviolet Disinfection Guidance Manual (UVDGM) by the U.S. Environmental Protection Agency (USEPA). On-site validation testing was successfully completed at the three facilities early in 2003.
Following the June 2003 publication of the Proposed UVDGM, the UV system configuration and validation results for the CCWA's Freeman Road WPP were analyzed under the UVDGM framework. A comparison to the Tier 1 requirements indicated that not all criteria were met, so a Tier 2 analysis was necessary. From the Tier 2 analysis, the UV safety factors and dose requirement were reduced by approximately 12 percent compared to the proposed Tier 1 dose requirement. From these analyses, the CCWA systems exceed all potentially applicable USEPA requirements, and the CCWA is providing enhanced public health protection as intended upon project inception. As a result of these analyses, significant comments, focused on simplifying the UVDGM and enhancing its ease of use, were submitted to the USEPA.
Document Type: Research Article
Publication date: January 1, 2005
More about this publication?
- Proceedings of the Water Environment Federation is an archive of papers published in the proceedings of the annual Water Environment Federation® Technical Exhibition and Conference (WEFTEC® ) and specialty conferences held since the year 2000. These proceedings are not peer reviewed. WEF Members: Sign in (right panel) with your IngentaConnect user name and password to receive complimentary access.
- Subscribe to this Title
- Membership Information
- About WEF Proceedings
- WEFTEC Conference Information
- Ingenta Connect is not responsible for the content or availability of external websites