CASE STUDY: TREATMENT OF SECONDARY EFFLUENT FOR USE AS COOLING TOWER MAKEUP AT A COMBINED-CYCLE NATURAL-GAS POWERGENERATING FACILITY
Abstract:FPL Energy's Rhode Island State Energy Partners LP (RISEP) has constructed a 540-megawatt combined-cycle, natural-gas-fired power plant in the town of Johnston, Rhode Island. During the development phases of the project, it was determined that an adequate potable and natural water supply was not available to supply makeup water to the power plant's cooling towers. As a result, RISEP established a working partnership with the neighboring community of Cranston, Rhode Island to use secondary effluent from the city's wastewater control facility (WCF), normally discharged to the Pawtuxet River.
The use of treated effluent in the cooling towers led the Rhode Island Department of Environmental Management (RIDEM) Office of Air Resources to issue stringent permit limits. The permit required the cooling tower supply makeup water to have a total suspended solids concentration (TSS) of 5 mg/l or less. In addition, the cooling tower makeup water was required to have a total residual chlorine (TRC) concentration of not less than 1 mg/l at the power plant (12 miles away from the facility). To meet these requirements, a filtration and chemical feed system were proposed to filter particulate matter from the effluent and to provide enhanced disinfection using sodium hypochlorite. These processes were incorporated into a tertiary treatment facility located at the Cranston WCF. RISEP's aggressive schedule required that permitting, design, construction, and start-up of the tertiary facility be completed in approximately 18 months. Design-build project implementation was selected as the best approach to meet the schedule requirements. M&E designed a tertiary treatment facility at the WCF and 12 miles of 18-inch ductile iron supply pipeline and 12-inch return pipeline for the cooling tower makeup and blow down and power plant wastewater discharge. The blow down is conveyed back to the WCF's headworks for treatment. The facility is designed to supply the power plant's cooling towers with an average flow of 2.5 mgd and peak flow of 4.3 mgd using three 450-horsepower pumps.
This paper provides a discussion of the project including an overview of the regulatory and technical requirements that drove the overall design basis for the supplemental treatment facility, high-pressure pipeline design considerations, features of the instrumentation and control system, and start-up aspects of the project.
Document Type: Research Article
Publication date: 2002-01-01
More about this publication?
- Proceedings of the Water Environment Federation is an archive of papers published in the proceedings of the annual Water Environment Federation® Technical Exhibition and Conference (WEFTEC® ) and specialty conferences held since the year 2000. These proceedings are not peer reviewed. A subscription to the Proceedings of the Water Environment Federation includes access to most papers presented at the annual WEF Technical Exhibition and Conference (WEFTEC) and other conferences held since 2000. Subscription access begins 12 months after the event and is valid for 12 months from month of purchase. A subscription to the Proceedings of the Water Environment Federation is included in Water Environment Federation (WEF) membership.
WEF Members: Sign in (right panel) with your IngentaConnect user name and password to receive complimentary access. Access begins 12 months after the conference or event
- Subscribe to this Title
- Membership Information
- About WEF Proceedings
- WEFTEC Conference Information
- Learn about the many other WEF member benefits and join today
- Ingenta Connect is not responsible for the content or availability of external websites