If you are experiencing problems downloading PDF or HTML fulltext, our helpdesk recommend clearing your browser cache and trying again. If you need help in clearing your cache, please click here . Still need help? Email firstname.lastname@example.org
A pilot study investigating the efficacy of low pressure, high intensity ultraviolet (UV) radiation for disinfection of urban wastewater was conducted. The pilot study utilized a small-scale version of the Ultra Guard UV treatment system provided by UV Systems Technology, Inc. (Burnaby,
Canada). The primary objective was to determine whether low pressure, high intensity UV irradiation could potentially be used to meet the California Water Reclamation Criteria (CWRC) for total coliform bacteria in reclaimed water and to determine its potential for a 99.99% reduction
of two model enteric viruses(MS2 coliphage and poliovirus). UV pilot unit inactivation of the total and fecal coliform bacteria, sewage indigenous F-specific coliphage, seeded F-specific coliphage (MS2), sewage indigenous enteric viruses, and seeded poliovirus type I in tertiary treated wastewater
was investigated. During the course of the pilot study, an infectious adenovirus was isolated from UV disinfected tertiary and secondary treated wastewater. The virus was detected in 15 of 16 experiments involving large volume (352-697 L)sampling and analysis for indigenous enteric viruses
and seeded poliovirus. The adenovirus was identified via electron microscopy and enzyme immunoassay after isolation using traditional cell culture based methods. Tertiary treated samples in which the adenovirus was detected received calculated UV doses in the range of 34-71 mW-sec/cm2.
Turbidity and total coliform bacteria levels in these samples were within the CWRC standards of <2 NTU and no greater than 23 MPN/100 mL for a single sample(30 d sampling period), respectively. Overall, total coliform bacteria were effectively removed from UV disinfected tertiary effluent
indicating that low pressure, high intensity UV irradiation could potentially be used to meet the stringent CWRC. Seven-day totalcoliform median values were not determined from the pilot unit data, however, a conservative estimate suggests that a dose of approximately 60 mW-sec/cm2
would be sufficient to meet the 7-d median concentration of no more than 2.2 MPN/100 mL for the last 7 samples taken. A 4-log10 removal of seeded MS2 and indigenous F-specific coliphage in the pilot unit experiments (tertiary effluent) was achieved at doses of 70 and 50 mW-sec/cm2,
respectively. The seeded poliovirus was not detected in UV treated secondary or tertiary effluents, however, problems with the concentration protocol prevented documentation of a specific 4-log10 removal of the virus. Comparative collimated UV irradiation studies indicated that
the isolated adenovirus was more UV resistant than MS2 coliphage and poliovirus type I. Doses of approximately 33, 112, and 183 mW-sec/cm2 were required to achieve a 4-log10 removal of poliovirus, MS2, and theisolated adenovirus, respectively. These findings indicate
that UV doses found to be effective at meeting the stringent CWRC total coliform standards may not provide suitable reduction of some naturally occurring pathogenic viruses such as adenovirus. Further research is needed to determine appropriate doses for UV disinfection of pathogenic enteric
viruses in wastewater.
Proceedings of the Water Environment Federation is an archive of papers published in the proceedings of the annual Water Environment Federation® Technical Exhibition and Conference (WEFTEC® ) and specialty conferences held since the year 2000. These proceedings are not peer reviewed. WEF Members: Sign in (right panel) with your IngentaConnect user name and password to receive complimentary access.